How Do I Know If The Boiler Is Big Enough To Service My Addition? - HVAC - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum > HVAC How do I know if the boiler is big enough to service my addition?
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

10-10-2008, 07:08 PM   #1
Newbie

Join Date: Sep 2008
Posts: 5
Rewards Points: 10

How do I know if the boiler is big enough to service my addition?

I have a V83 series burnham boiler that's about four years old. I am adding an addition to the house that would bring the size of the house to around 3000 square feet. I am not sure if the boiler I have will be large enough to service the added space.

10-10-2008, 08:35 PM   #2
Member

Join Date: Sep 2008
Location: Portland, OR
Posts: 1,186
Rewards Points: 500

Find out how many BTU's the furnace is good for. Calculate the total cubic feet (not square feet) of the area you want to heat. Divide the total cubic feet into the BTU's of the furnace.

If you are lower than 5 then you might consider a bigger furnace. If you are above 5 then you are golden.

You didn't mention where you live and that is a factor in your heating. If your climate is temperate then you could get by with a smaller furnace, if you are in a colder climate then a slightly larger furnace might be worth buying.

I have used this figure for years and it has worked so far. Deciding what size furnace is more of an art than science.

There are so many factors that determine the size of a furnace and I have listed them in previous posts.

__________________
My idea of a perfect day: No where to go and all day to get there.

10-10-2008, 09:06 PM   #3
Newbie

Join Date: Sep 2008
Posts: 5
Rewards Points: 10

Thank you

Thank you for the quick response Marvin Gardens. I'll post how it worked out.

 10-10-2008, 09:21 PM #4 Member   Join Date: Oct 2008 Location: Suburbs of Detroit Mi Posts: 3,704 Rewards Points: 2,000 What marvin suggest is ok , but the only way you'll find out for sure is to do a Manual J heat load calculation. There are many things to consider in sizing a piece of equipment. Exposure to wind, degree days , infiltration of air, window quality, height of ceiling, R value of walls and ceiling insulation. Rule of thumb is has to much fudge factor built into it so in many cases you end up going over the right btu rating, Do a google search on LOAD CALCULATION and visit the sites. There is one site where they will give you overkill info on load calcs, but I don't think I am allowed to post the link. Sorry Marv. Just a difference of opinion on sizing.
10-10-2008, 11:13 PM   #5
Member

Join Date: Sep 2008
Location: Portland, OR
Posts: 1,186
Rewards Points: 500

Quote:
 Originally Posted by hvaclover What marvin suggest is ok , but the only way you'll find out for sure is to do a Manual J heat load calculation. There are many things to consider in sizing a piece of equipment. Exposure to wind, degree days , infiltration of air, window quality, height of ceiling, R value of walls and ceiling insulation. Rule of thumb is has to much fudge factor built into it so in many cases you end up going over the right btu rating, Do a google search on LOAD CALCULATION and visit the sites. There is one site where they will give you overkill info on load calcs, but I don't think I am allowed to post the link. Sorry Marv. Just a difference of opinion on sizing.
No need to be sorry. There is a lot to sizing a furnace and more input is better than less input.

__________________
My idea of a perfect day: No where to go and all day to get there.

10-10-2008, 11:23 PM   #6
Registered User

Join Date: Apr 2008
Posts: 6,520
Rewards Points: 2,000

Quote:
 Originally Posted by hvaclover There is one site where they will give you overkill info on load calcs, but I don't think I am allowed to post the link.
No problem posting the link, as long as it isn't an advertisement for a user-affiliated site or product. If the link is to beneficial information that is pertinent to the thread, it is just fine to post it.

10-11-2008, 12:01 AM   #7
Member

Join Date: Oct 2008
Location: Suburbs of Detroit Mi
Posts: 3,704
Rewards Points: 2,000

Quote:
 Originally Posted by thekctermite No problem posting the link, as long as it isn't an advertisement for a user-affiliated site or product. If the link is to beneficial information that is pertinent to the thread, it is just fine to post it.
Thanks

HVAC-TALK.COM

Residential section is where to ask about the the Manual J calcs.

Please read the site rules as they are very strict on certain things.

They will be able to point you to a professional Manual J sizing for your addition or point you in the right direction to do one your self.

Good luck.
Clover.

10-11-2008, 05:50 AM   #8

Join Date: Oct 2008
Location: Somewhere
Posts: 34,592
Rewards Points: 8,170

A load calc will tell you if the current boiler can handle the load of both the addition and cuurent structure at the same time.

If its border line. Zoning can help it. If you use set back stats and don't need the whole house heated to the same temp 24/7.

The next thing that will hinder that boilers abilities. Is the circulator. It most likely has a Taco 007.(a factory standard with 90% of the boilers) Its GPM is too low for most installations.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post uncleneiler Plumbing 4 06-22-2010 09:01 AM stevedar Electrical 20 11-29-2009 08:14 PM jogr Electrical 18 09-24-2008 10:31 AM sgbotsford HVAC 2 12-01-2007 02:47 PM alexz Electrical 10 07-29-2007 10:00 PM

Top of Page | View New Posts