Honeywell L8124L Settings on Oil Boiler
My settings on the L8124L slant/fin oil boiler were set at Hi-170, Lo-150 and differential at 25, when would the circluator be running when there is a call for heat in the house?
Also, I have an Superstor Ultra indirect water tank connected as another zone for DHW, are the above settings correct for this type of DHW? Also, I have a wood boiler plumbed into this system, does the above settings seem correct for this as well?
Those settings are fine. I'd use a slightly lower setting with an indirect though. Since you don't need it as high for an indirect. Probably 130 for low.
|All times are GMT -5. The time now is 01:36 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.