HighEfficiency Furnace Shuts off before reaching target temperature
What is the brand name. Ducane or AirFlo? Hard to tell where the water is coming from but it may be the gasket behind the exhaust fan is faulty or a different problem. I would get the installer to fix it as removing the ventor fan is not easy and the gasket is not a easy DIY fix either. There should be a LED in a viewing window in the lower door. Check for an error code when it ias acting up. Check your vent pipes outside for obstructions.
That unit is a clone of a Lennox as they own those 2 brands. Get the installer to make sure it is sloped to the front 1/2 an inch for better drainage AND to make SURE they followed the installation instructions PERFECTLY for the condensate trap. If the vent pipe on the trap is too long they don't drain properly.
"Cut it twice and it is still too short".
To view links or images in signatures your post count must be 10 or greater. You currently have 0 posts.
Last edited by yuri; 01-21-2013 at 06:43 PM.