Help! with Concord 80+ gas furnace + T-STAT
( Scratchin' my head )
Air-conditioning unit = outside Type: Goodman
Furnace = in attic = Model: RGU80, RGH80, RGC80 per Manual
Part No. 42457E097
Furnace: Concord 80+ gas furnace
Air-conditioning worked fine, then stopped. Noticed
that the ( t-stat ) was off, ( no LED )
(t-state requires no battery's)
Checked all circuite brakers, and actually swapped out the
braker for the airconditioning unit at electrical panel.
( still no power to (t-stat) ) checked (t-stat) w/volt meter no power
Next: checked all circuites with volt meter, everything has power.
Checked power connection at furnace, and air-conditioning unit
all show power going to units.
( Circuites are not tripping )
Took off service panel of Concord 80+ furnace,
(troubleshooting lights ( slowly flashing green in unisen )
From the looks of it looks like the problem
is from the furnace to the t-stat. ( no power from furance to t-stat)
Looked for circuit braker on ( furnace control board ) and found
none. actually looked all over furance for circuit breaker ( type found in car )
and found nothing.
( please email me if you have information that could help )
Is there a reset on the furnace ?
Any help is much appreciated.
J in Cali.
|All times are GMT -5. The time now is 08:42 AM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.