||10-11-2007 07:31 AM
HELP: Bleeding Baseboards
HW mixed radiator/baseboard system. Radiators HOT, basboards barely warm at best even with Thermo up high. NO bleeders or valves except one bypass at boiler. Baseboards tapped off main line one side to feed other to return. Can't get air out of baseboards. Need guidance: Where do I put in bleeder for basebaoards? On the return side at elbow just before it goes into floor? IS there any other way to get air out of baseboards? I have pushed pressure up until PRV pops and run water through system with hose attached but air does not come out of baseboards. Thanks.. COLD in Chicago..