The main area needs 1900? but the bedrooms need 6,000 each?
You select registers that will have the throw you need and a low sound rating at the CFM you need. Generally you limit residential to less then 200 CFM per drop. At 6,000 BTUs it would take an 8" supply for the bedrooms.
You need a real load calc done, and not just guess.
The Following User Says Thank You to beenthere For This Useful Post: