||07-12-2005 05:02 AM
Heat pump problem
Last week I noticed my inside fan was not cutting off and the air it was blowing was not cool. I also noticed the outside unit was not running. I called a friend who used to do HVAC work and he told me it was the contactor. I replaced it and everything works fine until nightfall and then the outside unit will not start up. I have tried but not detected any sounds from the outside unit when this occurs. I will turn the system off and then when I restart it the next day it works fine again until nightfall. I have also changed the thermostat thinking that might have contributed to the problem. Anyone have any thoughts on the situation. I am hesitant about calling a service tech after being gouged by one a couple of years ago.
||07-22-2005 01:15 AM
what did you replace???program your temps right???a fan will continue to run ,to circulate air after the temp is reached ,for a while..on certain makes
|All times are GMT -4. The time now is 02:35 PM.
© 2003 - 2010 The Building Network LLC