I have a Goodman furnace and an Goodman airconditioning unit. I have replaced the thermostat with a honeywell digital thermostat RTH230B. I have also replaced the 2 single pair wire with a single 18 awg 5 wire. Since then nothing has worked but I have been able to get the furnace to work but the air conditioner does't work and the blower motor does't turn on when the fan switch is turned on.
My thermostat is wired:
Rh- red (jumpered)
Rc- red (jumpered)
W- White, Blue
My furnaced is wired:
W- White and Spillage switch
G- Green, Blue and relay
C- Relay and Gas Valve
I'm pretty good at reading schematics but I can't find any on my Goodman furnace. I would appreciate any help on my wiring probem.
you didn't label the wires when you took them off the original thermostadt ?
The only thing that I changed in my wiring is the blue wire that I jumpered from the green wire on my furnace and the white wire on the thermostat. If I lift the blue wire my gas turns on but my blower never turns on.
When the blue wire is lifted and I jumper the red-green-yellow wires the only thing that turns on is the blower motor, not the a/c unit.
When the red-white-yellow wires are jumpered the gas and blower turns on.
When the red-green wires are jumpered the blower turns on.
When the red-yellow wires are jumpered the blower turns on not the a/c unit.
goodman has an ongoing recall on some of their furnaces.you may be able to get a new furnace for the cost of the install.about 500.00bucks.check it out with a HVAC company who works with goodman.
|All times are GMT -5. The time now is 02:10 AM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved