my indicator light says open limit circuit what should i try
First and foremost change your filter. High temperature limit switches trip due to excessive heat internal to the furnace, 99.999% of the time due to lack of air flow and of that, 50% due to a clogged filter and the other 50% a dirty evaporator coil.
You're going to need a meter to ohm out each individual switch to find out which one it is. Sometimes they are resettable, other times you'd need to have it replaced.
|All times are GMT -5. The time now is 01:20 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.