gas heater trouble
I am having some trouble with my central heating unit.
When I turn it on and set my thermostat, I hear it start up and
the gas lights. But it burns for like 30 seconds then clicks off, this reapeats until I switch the unit off. Now it does not do this all the time
but the majority of the time it does. Any ideas?
It sounds like you have a new enough furnace to have a flame sensor. The flame sensor is a metal rod in front of the burner that is opposite of the ignition source, possible ignition sources are hot surface, direct spark, intermittent pilot. If the unit uses a pilot the flame sensor could be located in the pilot burner. Look for a rod that is about 1/8"-3/16", it should have a single wire coming off from it. The wire could be yellow or white and some manufacturers use a orange one. Once you verify what you are dealing with, unplug or shut power off to furnace, remove the rod from the furnace, use a wire brush and clean very well. ( use wire brush only, DO NOT USE SANDPAPER OR SANDCLOTH ). Reinstall the flame sensor, turn power back on to furnace, unit should operate properly. If it does not stop the problem it could be ignition system is failing. Not sure what type or model furnace you are working with, but if this does not work if you can give me the information, I can walk you through it.
Thanks a lot!
I will give this a try and see where it gets me.
The unit I have is a mobile home unit made by intertheme.
I think it is from the later 90's. It works great when it is working!
I'll keep you posted
|All times are GMT -5. The time now is 10:55 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.