||Thread Tools||Display Modes|
|12-07-2011, 03:41 PM||#1|
Join Date: Dec 2011
Posts: 1Rewards Points: 10
Gas Heater Problem - Temperature Differential
I'm having trouble with wide temp differentials in the house, especially in the master bedroom. At different times, very cold, others very hot. Didn't experience these wide differentials during the very hot Summer using air conditioning.
Details..hopefully this covers it:
New Home in North Texas
4600 Sq Ft
Zoned Gas Furnaces - two units
House insulated very well
There are only two large ducted returns in the house. They are in the ceiling, at about 10 ft level. Somewhat centrally located. Ceilings in some locations are vaulted up to around 14 ft.
Thermostats are located near the returns. They appear to be accurate and functioning properly.
One return / thermostat is located just outside master bedroom door. There is about 1000 Sq Ft of living space through master, into bath and closet. Lots of air pressure at the master door.
Nights start off on cold but around 3-4 am get very hot.
I have tried:
Matching the thermostat temps / schedules
Raising / lowering other thermostat
Leaving bedroom door open (problematic because of dogs, etc)
Hiring professional air balance service
Installing pass-thru vent above master bedroom door
Installing an additional return in the master
Installing thermostat w/ remote sensor(s)
Not sure if this falls under warranty. Should I go back at the builder with this complaint or it it relatively common?
Thanks for any guidance.
Last edited by jejagua; 12-07-2011 at 04:01 PM.
|12-07-2011, 06:34 PM||#2|
Join Date: Jan 2008
Location: Long Island
Posts: 3,630Rewards Points: 2,000
do you have programmmable stats check the times and temperatures and time changes if so....set the temps all the same to eliminate the changes see if it runs more consistant sleep to wake are yu set in auto for system or heat on the stat...just try heat on system fan auto in the problem area
|12-07-2011, 06:56 PM||#3|
Join Date: Feb 2007
Location: NW Ohio
Posts: 804Rewards Points: 500
the problem is the returns......centraly located returns are a very very bad idea.....
|Thread||Thread Starter||Forum||Replies||Last Post|
|window condensation||kmpittman||Windows and Doors||4||11-29-2011 10:10 AM|
|Never Seen This Before! Water Heater Problem Please Help||JOSH76||Plumbing||5||02-14-2011 09:13 AM|
|Water Heater Problem||mdong||HVAC||19||11-29-2009 11:53 AM|
|Electric Baseboard Heater Problem||goombie||Electrical||9||12-23-2008 01:13 AM|
|Electric Water Heater Problem||mw2727||Plumbing||4||08-21-2008 02:51 PM|