Furnace will not stop running
What could be the problem
BigJim Moved thread from Electrical to HVAC
are you melting or is it just the supply fan.:huh:..if your swetting pull the stat off the subbase lets hear back
If your too hot, remove one of the thermostat connections from the furnace.
Dis connecting "R or W" will show you that it's a thermostat or thermostat wire circuit problem if the burners then shut down..
If it's just the fan that won't stop, then a overheating furnace with a tripped limit is a common cause. Dirty filters?
Thermostat fan control on or shorting?
Let us know.
|All times are GMT -5. The time now is 04:03 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.