Furnace Sizing - HVAC - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum > HVAC furnace sizing
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

12-04-2009, 04:46 PM   #1
Newbie

Join Date: Dec 2009
Posts: 3
Rewards Points: 10

furnace sizing

i need to replace my furnace. i have a G.E. input 135,000 BTU's, 24 years old.
recently had an energy audit completed, they recommend replacing my furnace with a AFUE of 92% or higher.
live in anchorage, alaska. 3791 SF home.
one contractor tells me they do not make a high efficency furnace large enough to handle my needs and wants to install an American Standard 140,000 80% AFUE.
another contractor wants to install armstrong G2D95CT100X 95% efficient.
i am concerned, Will the armstrong will keep my house warm.
If my current furnace of 135,000 BTU's is 60% efficient according to my energy audit, then i need 135,000 x 60 % = 81,000 BTUs output.

12-04-2009, 05:10 PM   #2

Join Date: Oct 2008
Location: Somewhere
Posts: 34,594
Rewards Points: 8,174

Your furnace may have an AFUE of 60%. But its steady state will be much closer to 75 to 80%.

They do make 120,000BTU input 90% plus furnaces.

So 135,000 X 80%efficiency equals 108,000 BTU output.
120,000 X 90%efficiency equals 108,000 BTU output.

When it was at your areas coldest, or design temps. Did/does your current furnace run non stop. Or does it cycle on and off.

 12-04-2009, 05:40 PM #3 Newbie   Join Date: Dec 2009 Posts: 3 Rewards Points: 10 it cycles on and off. does not run continuously.

 12-04-2009, 06:09 PM #4 An old Tradesmen   Join Date: Oct 2008 Location: Somewhere Posts: 34,594 Rewards Points: 8,174 Then you don't need a furnace that has as much output as the one you currently have. So the 100,000 BTU input 92% may still be larger then you need.
12-04-2009, 07:23 PM   #5
Member

Join Date: Jul 2008
Location: NW of D.C.
Posts: 5,990
Rewards Points: 2,000

Quote:
 Originally Posted by dmkkwk it cycles on and off. does not run continuously.
How many minutes on, how many off?
92,000 BTU/hr running at 10 min on, 2 minutes off is putting out 92(10/12) = 77k BTU/hr.

Last edited by Yoyizit; 12-04-2009 at 07:28 PM.

 12-05-2009, 04:36 PM #6 Newbie   Join Date: Dec 2009 Posts: 3 Rewards Points: 10 Right now it is 19 degrees F. here. The furnace i have is not running much at all. Within the next few days i will try and keep track of it running, timing the on and off periods. The critical time is when it is minus -20 degrees for 10 days straight. I guess that is when i really need to know how much it is running. i will be back with more info.....
12-05-2009, 08:23 PM   #7
Member

Join Date: Jul 2007
Location: Portland, OR
Posts: 515
Rewards Points: 392

Quote:
 Originally Posted by dmkkwk Right now it is 19 degrees F. here. The furnace i have is not running much at all. Within the next few days i will try and keep track of it running, timing the on and off periods. The critical time is when it is minus -20 degrees for 10 days straight. I guess that is when i really need to know how much it is running. i will be back with more info.....

You can buy a hand full of units at 95% eff that may meet your needs. Here is a spec sheet for a goodman that you could install yourself if you wanted. It's not as hard as you might think.

http://www.goodmanmfg.com/Portals/0/.../SS-GMVC95.pdf

 12-05-2009, 09:08 PM #8 Hvac Pro     Join Date: Nov 2008 Location: Winnipeg, Canada Posts: 16,127 Rewards Points: 392 I would and I use Beentheres 80% rule. The input is one number but we heat our houses with the OUTPUT, not the input BTU'S. look at the output rating on the model # info inside your unit. Efficiency has to do with air leakage up the chimney in the off cycle etc. Not a factor with a high efficiency unit. It goes down to -40F where I am and we can get 30 mph winds. A 110,000 BTU high efficiency will be okay where I am. I would go one further and buy a 2 stage furnace. It will fire at 70% on low fire and use that for quite a bit of the heating season so the final size is not critical. We have sold some of the Armstrongs (Lennox owns them) and they are pretty good units. The AmStd is way oversized and will cost a LOT for \$\$ in fuel over several yrs in your climate. If your guy sells Lennox a G61, 110 would be a good choice (2 stage and 95% efficient) and is eligible for your rebates. The 100 Armstrong may be a bit small but it all depends on how good your windows, doors and insulation are. They make a 125 in that one. Last edited by yuri; 12-05-2009 at 09:20 PM.
12-06-2009, 08:35 AM   #9
Member

Join Date: Sep 2008
Location: PA
Posts: 167
Rewards Points: 150

Have a heat loss done with the loss numbers you acquired. That tells you the btu's required to heat your home. Than choose the proper size unit from there. I always use the Gross output or DOE output which are the same.
http://www.comfort-calc.net/faq.html

 Tags afue , furnace , sizing

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post Jim W HVAC 30 05-13-2009 08:38 PM Tommy2 HVAC 41 12-01-2008 01:55 PM hartkem HVAC 39 11-18-2008 01:45 AM Swolef HVAC 2 09-18-2008 11:07 AM DSimo HVAC 3 06-17-2008 07:24 AM

Top of Page | View New Posts