Furnace will come on and run fine sometimes. But does not always come on when it should. If you push the thermostat up to try and force it to come on it won't. If you set it on 70, sometimes when the temp drops it will come on, sometimes it won't. Bad thermostat? It works good when it comes on.
"I'm twisted, not sick. Sick implies, I'll get better"
Installing since 1973
remove the stat from the subbase see that R and W thats what the stat closes to run the heat..remove the W wire and touch it to the R the furnace should run if it short cycles or not at all it is the furnace....aas long as R/W it touching the furnace should run
The Following User Says Thank You to biggles For This Useful Post: