Freezing Suction Line
At the nonprofit I work for I noticed a dripping sound coming from above the drop ceiling tiles. I pulled the tiles to find missing insulation on the suction line going through the ceiling, about a foots worth. There was some ice buildup on the 90 degree joint. This spot has been missing insulation for 7 years without a problem, until today.
Would adding rubber insulation over the section solve the problem... or is it a sign something else is probably wrong and to call a technician?
The system is a Carrier 25HBR3 Heat Pump unit that only heats/cools one large meeting room.
Nevermind.... it ends up the unit has stopped cooling all together. That answers that question.
|All times are GMT -5. The time now is 04:36 PM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.