The fan motor to our AC condenser has stopped working and we are looking for a new one. The existing one is as follows:
MFG: GE MOTORS
EQUIP MFRS #: HC39GE232A
V: 208 - 230
We are trying to cross reference the above part, but are coming up empty. Can someone please advise us on what we should be looking for.
Thank you in advance.
are you sure its the motor thats no good ? did you ohm out the windings ect ?
Grainger is a good place to look or your motor.
Its possible its just the run capacitor that is bad, and your motor is ok. Should check before you get a new motor.
here is a cross reference off the Grainger web page..check the frame # off that exsisting motor...could be just the cap....if not still get a new cap with a new motor... http://www.grainger.com/Grainger/AO-...BaseItem=5GD99
Don't know if this applies, but I found the link via google
The motor he found was
|All times are GMT -5. The time now is 11:43 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.