Ducting problem for an HRV
Ok guys, Here's the problem.
I am retrofitting an old house with an HRV and cannot decide the best way to run the stale-air-ehaust.
Here's what I'm planning to do:
HRV located in basement of bungalow, run one 12"x3" wall stack up to the attic, and then, using a 12x3 to 6"round stack boot, spider 6" insulated ducting to the bathroom, kitchen, living room, and main bedroom using ceiling diffusers.
I also want to run a few diffusers to the basment.
I will be running the fresh air return through the existing furnace ducts.
Does this sound acceptable?
Will I achieve an adequate draw to the HRV using this method?
Please help me out with any suggestions or advice,
|All times are GMT -5. The time now is 02:37 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.