Crazy estimates... what's up???
Got another estimate on a new furnace for my building.
First guy: (highly recommended but didn't take any measurements)
125,000 BTU Trane $7900
Second guy: (I picked him out of the phone book... took tons of measurements)
TWO 125,000 BTU Goodmans twinned together... price unknown (he just came today). Sez there's no way a single unit could get the heat up to the third floor much less heat an uninsulated 3-brick-thick building.
The building is 3500s/f, no insulation except for the attic, all new windows.
BTW, second guy said that the furnace is all cast iron and the heat exchanger won't crack. Can this be true?
One more question... the reason the furnace isn't working is that the blower motor burned out. I took it off and took it to a motor repair place. He said it's 40 y/o and can't be fixed. He is prepping a new motor for me to get the place up and heated again. So... in the meantime, the burner is still going on and off but there's no blower. Is it bad for the furnace to not have the blower running? I am picking up the motor tomorrow.
Get one of their catalogues.
|All times are GMT -5. The time now is 11:53 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.