CPH - how does it work?
From a previous thread I posted, it was recommended I switch my old mercury for a digital 'stat. This I did, and I set the cooling CPH to 2. I guess the question is - how does the CPH really work? I have the honeywell RT2310B, which I don't think has that "auto learn" feature some other stats do.. so does that mean I'm supposed to get 2 cycles per hour max? Approximately 2 cycles per hour? Is it normal to get about 4 cycles anyway (I'm supposing this is possible), depending on outside temps and insulation?
CPH. is based on a 50% load.
That is the only time, that you should definitely get 2 CPH. As the outdoor temp increases or decreases(depending on season). The CPH your actually getting will increase or decreae.
On Honeywell thermostats, temp overides CPH.
|All times are GMT -5. The time now is 03:54 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.