- - control board?
||02-15-2010 06:34 PM
Trying to figure out if the control board is bad. inducer fan and blower fan run all the time even when i disconnect t wires at board even if i pull the plug harness with wires that go to gas valve,inducer switch and limits.Sounds like a bad board everything else checks out oh my voltage at the w on t stat is only 17v all others are 24?
||02-15-2010 08:09 PM
Is it a ComfortMaker furnace? Many furnaces will energize the blower and inducer motors if you have an open limit. Check for continuity through all the limits before you pull the board.
|All times are GMT -5. The time now is 12:50 AM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.