||08-31-2011 09:15 PM
Originally Posted by jaxbeachman
My condenser fan motor is running at half speed and my contactor is not engaged. When i start the unit up fan runs at full speed and compressor wont turn on. when i take the top off unit, compressor is smoking hot. Turn unit off and came back next day to let thermal reset and fire unit up and checked unit again smoking hot. replaced the capacitor and still the same issue. fan still runs half speed even when contactor not engaged and compressor wont run and hot to touch. any advise
Did you check the run capacitor? Did you check continuity between motor windings?
You'll need a meter, preferrabley digital, that shows continuity/ohms. All you need is one that "beeps" when continuity is present.
off, remove the lid of the condenser and remove wiring harness or wires from the compressor itself. Test continuity from each of the three terminals to the other, start to common, common to run and run to start. Do this after the system has not been running for some hours to make sure that the thermal overload switch is not open as that would show no continuity due to an open common if it's overheated and has an open thermal protection switch.
If the compressor is cool and there is not continuity between any and all combinations of the terminals then the compressor is shot.