Okie. Caps don't like to be shorted out. Makes a big spark. :D
On top of that, motor was bad. Found a nice HVAC electrician who would answer my question. If compressor kicks on, and fan spins backwards, motor is bad. If compressor doesn't kick on, then it's likely the compressor shorted out.