Combustion Air Calculation - HVAC - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum > HVAC Combustion air calculation
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

10-27-2011, 01:57 PM   #1
Member

Join Date: Jul 2011
Location: Maryville IL
Posts: 68
Rewards Points: 75

## Combustion air calculation

I understand the 50 cubic feet per 1000 btuh rating and to calculate that, but it's unclear to me how to take into account the doors enclosing the aclove'd space the gas appliances are in. If the doors were air tight, is that where the 1 square inch per 1000 btuh per opening comes into play. I've found it in the code but it reads as if they assume the aclove is open with no doors. Any typicall gas furnace and/or water heater is usually enclosed in an area with doors. Anyone have a better read on that part of the code?

10-27-2011, 02:08 PM   #2
Member

Join Date: Nov 2006
Location: Maryland (DC 'burbs)
Posts: 1,414
Rewards Points: 1,238

I don't have any numbers for you but here the code specs louvered doors for rooms enclosing furnaces and water heaters that draw combustion air from inside so the space communicates with the rest of the house. My 10'x10'x9' util room, that had a 87K BTUH furnace (since replaced with a direct vent model) and a 40K BTUH water heater, has such a door.

Quote:
 Originally Posted by kevsprojects I understand the 50 cubic feet per 1000 btuh rating and to calculate that, but it's unclear to me how to take into account the doors enclosing the aclove'd space the gas appliances are in. If the doors were air tight, is that where the 1 square inch per 1000 btuh per opening comes into play. I've found it in the code but it reads as if they assume the aclove is open with no doors. Any typicall gas furnace and/or water heater is usually enclosed in an area with doors. Anyone have a better read on that part of the code?

 10-27-2011, 03:56 PM #3 Member     Join Date: Oct 2006 Location: Minneapolis/St. Paul, Minnesota - Latitude 45.057 Longitude -93.074 Posts: 4,044 Rewards Points: 2,578 My 30+ year old townhouse has a utility room with a newer 80-85% gas gas furnace and a gas water heater. It was required to have a fresh air intake from the attic space that dumps into a 5 gallon pail as a prevention of syphoning the warm air out. - Solid door, but is usually open for convenience. No problems at all. It would have been nice to put in a high efficiency furnace with a ducted supply, but the extra efficiency would not be justified (even at -20F winters) because of the installation and cost. Dick

10-27-2011, 04:50 PM   #4

Join Date: Oct 2008
Location: Somewhere
Posts: 33,752
Rewards Points: 6,468

Quote:
 Originally Posted by kevsprojects I understand the 50 cubic feet per 1000 btuh rating and to calculate that, but it's unclear to me how to take into account the doors enclosing the aclove'd space the gas appliances are in. If the doors were air tight, is that where the 1 square inch per 1000 btuh per opening comes into play. I've found it in the code but it reads as if they assume the aclove is open with no doors. Any typicall gas furnace and/or water heater is usually enclosed in an area with doors. Anyone have a better read on that part of the code?

If the room with the furnace is attached to a room that has solid doors, then only the volume of the room with the furnace is used. If the door is a louvered, then the volume of the other area can be used.

 10-31-2011, 06:47 AM #5 Member   Join Date: Jul 2011 Location: Maryville IL Posts: 68 Rewards Points: 75 Thanks for the input! I have recent learned from a local HVAC contractor that the prefered method is to use two 6 inch pipes (PVC or metal duct), one near the floor & one near the ceiling terminating in an upside down candy cane configuration. The two pipes exit the ceiling/wall and terminate into an 8 inch pipe and exit the roof. I really wish I could get a pic of this! The code reads that the two pipes (air sources) must be independent of each other though. We operate off of 2003 code where I live but its hard to tell if anyone is really following it

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post DIYerIT HVAC 2 07-30-2011 05:39 PM denemante HVAC 2 05-09-2011 04:22 PM rodney23 HVAC 6 02-13-2011 10:38 AM okrite HVAC 8 01-07-2010 10:58 AM RM575 HVAC 9 07-04-2007 01:37 PM

Top of Page | View New Posts