I have searched the internet for this problem and have not even seen it described.
I have a Coleman 8665D766 down draft mobile home furnace in my garage. Late last spring, the main blower motor died, and the furnace went through a couple of high-temp shutdowns before I noticed. This is an older furnace that has no electronics in it, and no adjustable controls. It is entirely controlled by temp limit switches.
I have since replaced the main blower and the furnace works again. However, it now short cycles during it's cool-down period:
1. Thermostat calls for heat.
2. Burners ignite, combustion blower starts.
3. Main blower starts after combustion chamber heats up.
4. Thermostat reaches desired temp.
5. Burners terminate, combustion blower stops.
6. Main blower continues for a minute or two.
7. Main blower stops for about 5 seconds.
8. Main blower starts again for just long enough to spin up to full speed (2 seconds?)
9. Steps 7 and 8 continue until combustion chamber is cooled off.
I am guessing that one of the limit switches was damaged during the high-temp shutoff periods last spring. I cannot find a manual for this furnace, but there is a wiring schematic on one of the covers that I can reproduce and post if needed.