Cold air return, or not?
We have a small bungalow house, at one time a small addition was put on the back (10 x 18) there is one heat vent in that area (center of long wall on outside wall), no cold air return. then entrance to this area is along one end opening of about 6'), through ther kitchen. The problem seems to be in the cold weather there is a draft along the floor of the kitchen coming from the added room, should I add a cold air return in there, or would it just be defeating the purpose of the heat vent that is in there? thanx.
If the cold draft is only when the heating system is running. then yes, a return in that room will help stop, or minimize the draft.
If you have that draft even when the heating system is not running, then a return won't help much if any.
In which case. You should recheck, how well sealed that room is. Since the cold draft could be from infiltration from around teh door or windows.
|All times are GMT -5. The time now is 09:59 PM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.