CFM Measurements For Return And Supply Grids - HVAC - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum > HVAC CFM measurements for Return and Supply grids
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

09-07-2011, 05:44 PM   #1
Member

Join Date: Oct 2010
Location: Austin - Texas
Posts: 1,402
Rewards Points: 500

## CFM measurements for Return and Supply grids

A/C 2,5T
Return Grid 31x14 (total area)
29x11 (open area) = 2,5 feet x 0.9 feet = 2,250 ft2
1332 CFM
592 FPM

How do I test on the supply? Do I have to measure the area from round duct or the grid?
Attached Thumbnails

__________________

**Always kill the power ** Hot air rises, but heat will always move from higher to lower temperatures. ** Real man shoot in manual. ** If it ain't grounded, it ain't dead.

09-08-2011, 02:34 PM   #2
Newbie

Join Date: Sep 2011
Posts: 24
Rewards Points: 10

You can use a surface measurement (or slide chart reference available by almost every manufacturer) on how much air can go through the supply registers. That's the same for ducting, usually that is in a wheel form for flex.

Is that a vane ammeter? You can do a quick check that will "ball park" your cfm to a zone. This is typically what inspectors will do.

To get a true reading you will also need to dig deeper into this with a tube reader in each branch of the supply ductwork.

Ultimately it's two things that really matter;

1. Cfm at the supply
2. Overall static pressure

09-08-2011, 03:37 PM   #3
Experienced

Join Date: Dec 2010
Location: Southern Michigan
Posts: 2,822
Rewards Points: 2,000

Quote:
 Originally Posted by JJboy A/C 2,5T Return Grid 31x14 (total area) 29x11 (open area) = 2,5 feet x 0.9 feet = 2,250 ft2 1332 CFM 592 FPM How do I test on the supply? Do I have to measure the area from round duct or the grid?
JJ--

29x11 = 319 in2
319/144(in2 per 1 ft2) = 2.215 ft2

You would then have to apply a "K" factor for the grill say .8

So

2.215 x .8 (K Factor) = 1.77 Ft2

1.77 Ft2 x Velocity = Volume

You can apply the exact same principle to the supply air registers and then total the supplys up.

You will also need a slack tube to measure static pressures in the system.

Keep in mind that the accuracy of a vane anometer is less than 90%.

Mark
__________________
When its all said and done there is usually more said than done

Last edited by Jackofall1; 09-08-2011 at 03:41 PM.

09-08-2011, 04:51 PM   #4
Member

Join Date: Oct 2010
Location: Austin - Texas
Posts: 1,402
Rewards Points: 500

Quote:
 Originally Posted by Dr.HVAC You can use a surface measurement (or slide chart reference available by almost every manufacturer) on how much air can go through the supply registers. That's the same for ducting, usually that is in a wheel form for flex. Is that a vane ammeter? You can do a quick check that will "ball park" your cfm to a zone. This is typically what inspectors will do. To get a true reading you will also need to dig deeper into this with a tube reader in each branch of the supply ductwork. Ultimately it's two things that really matter; 1. Cfm at the supply 2. Overall static pressure
CFM at the supply = Velocity x area of the supply grid - How to I know if duct is correct?

Overall static pressure:

Can I use digital manometer at return and supply ?
__________________

**Always kill the power ** Hot air rises, but heat will always move from higher to lower temperatures. ** Real man shoot in manual. ** If it ain't grounded, it ain't dead.

09-08-2011, 05:06 PM   #5
Member

Join Date: Oct 2010
Location: Austin - Texas
Posts: 1,402
Rewards Points: 500

Quote:
 Originally Posted by Jackofall1 JJ-- 29x11 = 319 in2 319/144(in2 per 1 ft2) = 2.215 ft2 You would then have to apply a "K" factor for the grill say .8 So 2.215 x .8 (K Factor) = 1.77 Ft2 1.77 Ft2 x Velocity = Volume You can apply the exact same principle to the supply air registers and then total the supplys up. You will also need a slack tube to measure static pressures in the system. Keep in mind that the accuracy of a vane anometer is less than 90%. Mark
So If I don't have the K factor the area will be:

(29x11)/144 right?

If I have the K factor the area will be:

{(39x14) x K factor }/144 right?

Can I use my digital manometer to get static pressure?
Attached Thumbnails

__________________

**Always kill the power ** Hot air rises, but heat will always move from higher to lower temperatures. ** Real man shoot in manual. ** If it ain't grounded, it ain't dead.

09-08-2011, 05:25 PM   #6
Newbie

Join Date: Sep 2011
Posts: 24
Rewards Points: 10

Sounds ok to me, again, check for the resistance levels from the mfg. Assumptions make the whole process a time consuming guess.

I use a u tube. I have had a few digital manometers but still feel a more accurate constant on the liquid tube (the internals of an old diaphragm just sketches me out)

Technically, static pressure is made of averaging several measurements on the supply/return side....I do mostly residential and am fairly happy to get three that are decently spaced from the equipment.
Testo has some good videos on how to use their products on trunks for accurate readings (I haven't looked, I bet they're on YouTube)

Hope that helps

Last edited by Dr.HVAC; 09-08-2011 at 05:29 PM.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post mysterylectric Plumbing 8 01-17-2012 11:19 AM atlantatd HVAC 4 04-13-2011 08:30 PM DanDaMan HVAC 6 12-11-2010 02:26 PM Kurt123 Plumbing 2 09-05-2010 09:48 PM hsl Building & Construction 0 11-18-2009 09:21 AM

Top of Page | View New Posts