Originally Posted by Master of Cold
Top slot is auxillary heat size. It should tell the kw on heater plate
Next slot is condenser size-look on condenser for model number if it is still there
Set the next one for heat pump -eff
Next set cfm at low
Lastly set for enh(anced)
You my friend are THE MAN!
They where all hooked up wrong except for CFM. The installer just went to the first pin on the right and hooked them up. (board is upside down) What an idiot!
Only one I'm not sure of is the condenser hp, I'll pull the cover off in the morning and get that.
The AC fan still will not cycle off, wonder if the incorrect hook up has screwed something up in the fan control?
I need to look at the thermostat wiring also.