a/c unit tripping
Does it end up in the soft reset middle position where you have to push it to off and then on. Or does it hard trip to the complete off position, Soft trip is from too much amperage draw. Hard trip is usually a dead short. Low voltage, loose or burnt wires etc inside the unit, stiff compressor, weak capacitor. Most units have a 5 yrs parts warranty so I would call the installer and have him properly check it.
"Cut it twice and it is still too short".
To view links or images in signatures your post count must be 10 or greater. You currently have 0 posts.