


Thread Tools  Display Modes 
02142012, 08:27 AM  #1 
011010100110111101100101
Join Date: Jan 2011
Posts: 244
Rewards Points: 150

BTU calc
I'm curious if I can get a calculation based on the following information.
Outside temperature is 18* F Inside temp is 56* F. Building is being heated with a 1200w (4000btu) electric heater. From this information, can I determine the required BTU to maintain 72* ? Is the heat loss linear?  Joe Advertisement 
02142012, 08:52 AM  #2 
Member
Join Date: Oct 2007
Location: Manitoba, Canada
Posts: 343
Rewards Points: 266

BTU calc
You can't predict that your heat loss will be linear. As the temp difference rises between indoor and outdoor your heat loss will also increase. This doesn't say anything about infiltration air due to wind,doors and building openings, exposure variables etc... You need to have a heat loss for the building completed to give you an accurate number.
Advertisement 
02142012, 09:08 AM  #3  
011010100110111101100101
Join Date: Jan 2011
Posts: 244
Rewards Points: 150

BTU calcQuote:
However, I was curious about what I'm actually seeing. Because the the software calculated more BTU per room than what appears to be lost. The area in question, roughly 700 sq ft, had a calculated loss of 21k at a design temp of 72* and 20* outside.  Joe 

02142012, 09:12 AM  #4  
Part of the Clover Leaf
Join Date: May 2011
Location: NW Burbs of Detroit Mi.
Posts: 1,107
Rewards Points: 500

BTU calcQuote:


02142012, 09:21 AM  #5  
011010100110111101100101
Join Date: Jan 2011
Posts: 244
Rewards Points: 150

BTU calcQuote:
Well the furnace is purchased, so that is that. What I bought the software for was mainly to size the ducts accordingly. The science behind forced hot air, and AC duct/register sizing is absolutely amazing.  Joe 

02142012, 09:23 AM  #6 
Member
Join Date: Oct 2007
Location: Manitoba, Canada
Posts: 343
Rewards Points: 266

BTU calc
So what size of furnace did you buy?

02142012, 09:41 AM  #7 
011010100110111101100101
Join Date: Jan 2011
Posts: 244
Rewards Points: 150

BTU calc 
02142012, 01:53 PM  #8  
Member
Join Date: Jul 2008
Location: NW of D.C.
Posts: 5,990
Rewards Points: 2,000

BTU calcQuote:
http://www.koubacavallo.com/bnchmrk.htm Your one day temps give you HDD, you know the 4000 BTU and so you can figure your avg. heat loss. Then rework the BTU to get the higher temp. diff. It's more accurate if your temp. diff. is averaged over a month or so. What's your sq. ft? 

02142012, 02:00 PM  #9  
011010100110111101100101
Join Date: Jan 2011
Posts: 244
Rewards Points: 150

BTU calcQuote:
The old section of the house, is around 900950 sq feet. An 80k wood stove will produce 86+ degree temps on a 15 degree day if I don't choke it down. I've done a heat loss calc on the old part based on windows and insulation, and it will require a bit more BTU than the new section of house.  Joe 

02142012, 04:21 PM  #10 
Civil Engineer
Join Date: Mar 2009
Location: Boston
Posts: 4,306
Rewards Points: 2,190

BTU calc
You can get a reasonable approximation to your original question as follows. The steady state heat loss through a wall, based strictly on conduction, is directly proportional to the temperature difference between the inside and the outside. By increasing the inside temperature from 56 degrees to 72 degrees, you are increasing delta T from 38 degrees F to 54 degrees F, which means you need approximately 40 percent more BTU/HR to maintain temperature.
This ignores several complexities, including the fact that the walls, floor and ceiling all have different R values. It ignores the fact that conduction and convection do not follow the same heat loss equations as radiation. And it ignores transient temperature issues, such as heating up and cooling down the space. But the answer, namely 40 percent more BTU/HR required, may be close enough for your use. By the way, unless your electric furnace runs at full capacity continuously, you cannot assume that you use the full 4000 BTU/HR, you may use significantly less. But if it runs continuously, my computation suggests you need about a 5600 BTU/HR heater to heat to 72 degrees F., assuming the geometry and insulation in your house do not change. 
02142012, 04:52 PM  #11  
011010100110111101100101
Join Date: Jan 2011
Posts: 244
Rewards Points: 150

BTU calcQuote:
I'm assuming the electric space heater is running full blast 24/7 because the temp only rises as it gets warmer outside, and falls as it gets colder outside. But I don't know the intended duty cycle of the heater, as I don't have a manual for it. Thanks again!  Joe 

02142012, 05:31 PM  #12 
An old Tradesmen
Join Date: Oct 2008
Location: PA
Posts: 26,526
Rewards Points: 4,690

BTU calc
If that 18°F outdoor temp is at night time when there is no solar gain. You can do a linear plot to determine heat loss for design conditions, and be some what reasonably accurate. Infiltration will increase as the indoor temp increases due to stack effect. So it will be slightly low.
Since 1200 watts is maintaining a 38 degree difference from outdoor temp. 2400 watts (8,191 BTUs) should be able to get you to 72 when its 18 degrees outside, and not have to run 24/7 to do it. Advertisement 
Thread Tools  
Display Modes  


Similar Threads  
Thread  Thread Starter  Forum  Replies  Last Post 
Load calc  anesthes  Electrical  49  09242011 06:43 AM 
Proper HVAC load Calc.  ChrisDIY  HVAC  2  05312011 10:06 PM 
Ampacity calc for laundry  WillK  Electrical  1  01032011 04:09 PM 
voltage drop/box fill calc  qbert  Electrical  4  01232010 11:24 PM 