Bryant Furnace Blower Running Constantly
On the 821 relay you will see a little pointer sticking out of on end of it. With the furnace plugged in if the blower keeps running. Take your finger and push this pointer to the left if the pointer is on to and to the right if its on the bottom. The blower should kick off. If it does you know for sure that this is your problem. The 821 relay is still available and is not all that exspensive. You could probably find it in one of these parts sites that are offered to you through this chatroom. I would not spend any more money on this furnace than you have to as it does not have much more life left in it. And you could afford to put a 90 plus Carrier in for what this thing cost you in gas for about two years.
Character is doing the right thing even when no one is looking. Intelligence is understanding and practicing the meaning of character.