||12-29-2012 06:51 PM
Bryant 90 plus furnace trouble
My furance seems to producing enough heat and warming the house well. I noticed about 3 days ago it sounded like it was pulsating. The vents sounded clear. I almost could feel it in the floor. Went downstairs no trouble codes. Also pulsating was barely noticable in the basement. Once the heat was off i turned on the fan to see if it would still pulsate. Nothing. Any suggestions??
||12-30-2012 09:16 AM
Fan wheel is coming apart from the hub. Check the play of the wheel from the hub. Be careful it can get worst if you play with it too much.
||12-30-2012 01:19 PM
Very common for older 90's to start cracking where inducer wheel is molded to metal hub, which attaches to inducer motor.Usually wheel just needs replacing, but due to age , the hub is rusted to motor shaft, so you end up replacing motor also.I've gotten to a point where I quote motor and wheel every time ,and if I get lucky and wheel comes off, clients bill is cheaper.
|All times are GMT -5. The time now is 12:36 AM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
Search Engine Friendly URLs by vBSEO