||11-27-2012 05:30 AM
Beckett Oil Burner
I have a beckett oil burner. I have this int. problem. At times the furnace does not light off. I have troubleshoot the problem down to the cleancut pump. The question I have is I don't know if the problem is the pump or the solinoid. If I tap on the pump the furnace will run.
||11-27-2012 10:08 AM
check wire connections to solenoid..may be loose and make contact when tapped..could also be sticking solenoid. if so replace it.
|All times are GMT -5. The time now is 03:06 AM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.