Bang, right before inducer draft motor starts
I just got a new Goodman high efficiency 95% furnace installed 2 days ago. It worked nicely from the start, but now two things are starting to worry me.
#1. It seems the inducer draft motor/fan is running louder. - is that normal?
#2. (This just started about 3 hours ago) There is a noticable "bang" in the furnace right before the inducer draft motor starts. Is that normal? It wasn't there before.
Could be something fell into the inducer. Call the guys back who installed it.
|All times are GMT -5. The time now is 06:02 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.