Aprilaire 400 not working
I have an Aprilaire 400 connected to my HVAC/forced air heating unit which doesn't seem to be working. I've tried the following:
- Followed instructions from Aprilaire to test/check the humidistat. I hear the clicks, but don't see any water coming out.
- Changed the water panel, however the humidistat 'change water panel' light is still on (see attached picture)
- checked the water pipes and pump but see no obvious problems.
I live in Long Island NY, and the inside humidity is 25% irrespective of the outside humidity.
It'll be great if any DIY experts can let me know if I can do anything else before calling a professional to look at it.
Thanks in advance for your help
remove the water lines from the solenoid valve. Incoming side inside the valve is a screen. use a screw to get it out. it may be plugged. on outgoing side of valve is a orifice. It may also be plugged
Thanks, I'll try it and post the results.
|All times are GMT -5. The time now is 06:49 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.