another question for a miller furnace problem
the furnace is running good but have now found out that there is alot of dirt and rust particles and slime from the contents of the fuel tank. ( which is located outside ) can i install another filter cartridge and not use a filter in it to catch the particles as they are heavier than the fuel, and use it as a catch basin so it doesnt clog the nozzle, and nozzle tip to cause the furnace to stop running due to lack of fuel? am going to replace the tank in the spring but want to try something now to keep things clog free till end of the heating season. am going to use an anti microbial solvent to eliminate the slime but not sure about the sediment problem. CARRIERMAN or anyone have any ideas?? :confused1:
rusty your the furnace guru your advice is keeping my family warm thru the 20 below weather we are having here in nw wisconsin thank you again.:thumbup:
General makes a nice little in line filter that you can use a wool filter in. The filter is washable or replaceable. The one that I prefer to use is part number S254 or 2A700A. In most cases the S254 is more than adequate. The filter housing and cartridge come pre assembled.
|All times are GMT -5. The time now is 11:12 PM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.