||06-30-2010 05:16 PM
american standard freedom 80 a/c issues
Hi i have 2 of these furnaces working together. When the a/c is on only one will turn on and cycle cool air. The fan on the other won't energize. Just wondering if I have the thermostat wires in the right location? any ideas?
Did you change the thermostat or any of the wiring? Those units should have a twinning terminal and feature on the circuit board on them to interlock them.
|All times are GMT -4. The time now is 06:51 PM.
© 2003 - 2010 The Building Network LLC