Air Conditioner Condensation Issue
I've got two Trane indoor coils installed and have a condensation issue with one of them. The unit is laying horizontal with the condensation drainline attached to one of the lower threaded openings. The other 3 threaded openings are NOT capped and the lowest one (next to the drain line) is leaking condensation into the overflow pan. Should these three openings be capped ???
Yup and most of Tranes units specify they must also be trapped in the horizontal position. Need to get your contractor back out and fix it right.
|All times are GMT -5. The time now is 11:21 AM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved