3 ton heat pump split 10 seer
have a unit that one day it runs fine,and then later it doesn't. pressures are 70/250 new filter.unit was low and injected w dye found signs of dye near acess ports but nothing confirmed weather it was blow bk from disconnection or leaking? i'm thinking maybe limit switch .don't know alot on cycles of a heat pumps,do they go into defrost during summer?
||07-12-2011 09:01 PM
No defrost in the cooling mode. High pressure switch trips around 400 psi so 250 shouldn't be an issue. Subcool and super heat checked to confirm charge and txv operation? Capacitor checked? Amps checked on condensor fan motor? Float switch on the condensate line or pump? Intermittent problems stink!
Yeah it makes for a long day on a roof when it won't show it's evil side. Just got to baby sit til it does,i guess. Will post what i find later
|All times are GMT -5. The time now is 03:17 PM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
Search Engine Friendly URLs by vBSEO