Unit starts up..igniter glows burners fire up but the gas flame shuts off after about 6 seconds...replaced the flame censor and still same problem..I'm thinking it could be the gas regulator or a bad board..any input from anyone would be appreciated thanks
Make sure the ground wire is tight and clean. Make sure the flame sensor is in direct path of the flame. If all of this tests good but same thing than the board is not doing it's job, time for a control board.
Last edited by Doc Holliday; 10-25-2012 at 12:10 AM.
The Following User Says Thank You to Doc Holliday For This Useful Post: