Insulation Question Please
I recently acquired a small home between Austin Tx and Dallas Tx that has the paper or vapor barrier facing up into the attic. It is stapled like crazy.
I want to add more insulation. Can I cut slits in the vapor barrier and blow in the blow in insulation or do I have to remove the old batts ? Any advice will be appreciated!
Thanks in advance
Is the ceiling sheet rock? Isn't there an access panel to allow you to get up there? Trying to picture what you are saying is difficult, photos work wonderful.
Remove the vapor retarder paper facing, none is required for your location; http://www.buildingscience.com/docum...commendations/
Is the HVAC up there? http://www.buildingscience.com/docum...e-humid-south/
Just slashing the paper does nothing; "Furthermore, the amount of vapor which diffuses through a building
component is a direct function of area. That is, if 90 percent of the
building enclosure surface area is covered with a vapor retarder, then
that vapor retarder is 90 percent effective. In other words, continuity of
the vapor retarder is not as significant as the continuity of the air barrier.
For instance, polyethylene film which may have tears and numerous
punctures present will act as an effective vapor barrier, whereas at
the same time it is a poor air barrier. Similarly, the kraft-facing on fiberglass
batts installed in exterior walls acts as an effective vapor retarder,
in spite of the numerous gaps and joints in the kraft-facing." from; http://www.buildingscience.com/docum...researchreport
|All times are GMT -5. The time now is 10:47 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.