Vapor Barrier in Basement with XPS Rigid Foam?
I know all the sites say to not use a vapor barrier if using the 2" XPS directly to the foundation walls method, but my building inspector for my town in upstate NY says it will still be required and recommended using paper-backed fiberglass insulation in the 2x4 wall.
I'm certainly not going to win an argument with him, so I am curious, is this really that bad or am I fine doing this? Just wondering if anyone came across the same thing.
After some specific research for you, I found; 2010 (which you are not under yet) doesn't require any BELOW grade; http://publicecodes.cyberregs.com/st...0_4_par036.htm
Your 2007 State Energy Code says- #3. Where other approved means to avoid condensation (which is foamboard); http://publicecodes.cyberregs.com/st...7_4_par028.htm
Found it, 402.5 says ABOVE grade walls require vapor retarder/barrier; http://www2.iccsafe.org/states/new_y...y_frameset.htm
Show him/her the other code year print-outs and BSC for possibly letting you skip it, OR have them show you exactly where it says it is required BELOW-GRADE...
find another inspector who is up to date. surely you are not stuck with just one, are you? hopefully, not, or at least this cat will learn.
|All times are GMT -5. The time now is 11:11 AM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved