Roof venting around can lights
I have an addition on my house (12x15, 4 season room) that has a cathedral ceiling. I have installed can lights in a few of the rafter bays which will make installing roof baffles difficult. How important is it to vent every bay, and if I dont vent the few bays with cans in them, should I still hold the insulation off the roof sheathing by an inch? The cans are airtight IC cans. Thanks
Every rafter bay requires venting. Where are you located?
+1 on venting every bay.
We just stripped a roof that was a cathedral roof with can lights (not airtight) and the rot was most concentrated in the rafter bays that became obstructed (insulation batt falling down) and had the can lights.
Can lights, regardless of airtight or not, will be a big short circuit in the insulation layer and will be points of additional moisture because of the interruption in the vapor retarder and lower than average R-Value. Even if you don't think there is air leakage, there probably is.
You need to vent each bay.
|All times are GMT -5. The time now is 07:13 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.