||Thread Tools||Display Modes|
|03-30-2013, 10:57 AM||#1|
Join Date: Jan 2012
Location: Pacific North west
Posts: 1,311Rewards Points: 626
New code requirement
Was at a local training for energy codes. And this will tick off the sheetrockers.
No more inset stapling of the batts. New code face stapling of the batt is required per the 2009 energy code. Just thought I would pass this on. Does not bother me in the least.
|03-30-2013, 05:54 PM||#2|
Join Date: Apr 2012
Location: Fairhaven, Massachusetts
Posts: 2,914Rewards Points: 2,106
we've had that issue locally the past year with guys not understanding the sealing requirements.
"You get what you pay for, and sometimes free costs more!"
|03-30-2013, 06:37 PM||#3|
Join Date: Nov 2011
Location: Hartfield VA
Posts: 32,943Rewards Points: 11,012
Being a layman it just makes more since to me to do it that way and less likly to put holes in the insulations vaper barrier that way.
|03-30-2013, 06:38 PM||#4|
Join Date: Aug 2011
Location: Washington DC Metro Area (VA, MD, DC)
Posts: 12,464Rewards Points: 3,822
Things are getting tighter these days.
There are entire companies dedicated to helping the builders meet the new codes.
|03-31-2013, 08:46 PM||#5|
Join Date: Mar 2009
Posts: 11,284Rewards Points: 4,634
I think it came up in response to this; https://docs.google.com/viewer?a=v&q...9yRrrdP1VBztDg
OTOH, lol; "4.2.1 Insulation batts and blankets or the flanges of insulation batts or blankets shall not be applied to the face of framing members to which gypsum panel products are to be attached.” From; http://www.lafargenorthamerica.com/G...%20English.pdf Is the current version up-dated with a change?
For those that think the facing requires stapling/complete coverage like an air barrier rather than a vapor barrier/retarder;
"Magnitude of Vapor Diffusion and Air Transport of Vapor
The differences in the significance and magnitude vapor diffusion and
air transported moisture are typically misunderstood. Air movement as
a moisture transport mechanism is typically far more important than
vapor diffusion in many (but not all) conditions. The movement of water
vapor through a 1-inch square hole as a result of a 10 Pascal air
pressure differential is 100 times greater than the movement of water
vapor as a result of vapor diffusion through a 32-square-foot sheet of
gypsum board under normal heating or cooling conditions (see Figure
In most climates, if the movement of moisture-laden air into a wall or
building assembly is eliminated, movement of moisture by vapor diffusion
is not likely to be significant. The notable exceptions are hot-humid
climates or rain wetted walls experiencing solar heating.
Furthermore, the amount of vapor which diffuses through a building
component is a direct function of area. That is, if 90 percent of the
building enclosure surface area is covered with a vapor retarder, then
that vapor retarder is 90 percent effective. In other words, continuity of
the vapor retarder is not as significant as the continuity of the air barrier.
For instance, polyethylene film which may have tears and numerous
punctures present will act as an effective vapor barrier, whereas at
the same time it is a poor air barrier. Similarly, the kraft-facing on fiberglass
batts installed in exterior walls acts as an effective vapor retarder,
in spite of the numerous gaps and joints in the kraft-facing.
It is possible and often practical to use one material as the air barrier
and a different material as the vapor retarder. However, the air barrier
must be continuous and free from holes, whereas the vapor retarder
need not be." From; pp.5, http://www.buildingscience.com/docum...researchreport
If any ads are present below my answer or words underlined/colored, I do not condone/support/use the product or services listed/linked to, they are there without my consent.
17,000 dryer fires a year, when did you last clean the inside of the dryer near motor or the exhaust ducting?
|The Following User Says Thank You to Gary in WA For This Useful Post:||
|Thread||Thread Starter||Forum||Replies||Last Post|
|Automatic Closet Lights||Sav505||Electrical||52||12-28-2012 07:24 AM|
|code requirement for distance b/ween recessed lites and bath tub||amakarevic||Electrical||2||11-24-2011 06:10 AM|
|Lighting proximity to outdoor hot tub - Code Question||jeffinpickering||Electrical||0||09-12-2011 01:43 PM|
|Bryant Plus 90 Code 31||~kirkland~||HVAC||1||03-08-2011 06:14 PM|
|Distance between Heater & Combustibles||DIY_JC||Building & Construction||7||01-20-2009 07:52 AM|