drywall problem, need immediate answer please
my 80 yr old dad wants to save money and put over another layer of dry wall instead of tearing down the old wall. Its an issue of a cold room that also gets too hot. someone wants to charge 4000 dollars to tear down walls ntall insulation and new floor and ceiling waht should we do? my email is email@example.com my dad is flipping the bill and he is impatient and naive. He is not a good decision maker
How much and what type of insulation is in the wall now? In the floor? In the ceiling?
Is there siding on the walls?
Where do you live (State/Country)?
What type of heating system?
Explain the Contractor's ideas......
Be safe, Gary
An extra 1/2" of drywall will not solve your insulation woes.
Drywall stops air gaps though does little to stop thermal penetration.
Do you have insulation anywhere in the room now?
mmm...i know we're taught drywall is not insulation but it does serve as an air block. if you've ever been in a house with the roof on but no drywall yet in the middle of summer there is just an enormous difference when they are done with drywall. going from 1/2 to 1" however will do next to nothing. once the first layer is there it is what it is.
as for your situation, is there a reason it needs to come out? mold? water penetration? some reason that requires a tear out?
if it's just a lack of insulation, well, depending on the framing it's hard to say how much will even go in there. you can get up to r15 in a 2x4 wall which is much better than nothing but 4000 will pay for a lot of extra electricity if you add a heater and ac to the room.
is this room setting outside the main house or somehow exposed heavily outside? also, how much glass is in it?
|All times are GMT -5. The time now is 01:18 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.